City of Calgary, Alberta
The City of Calgary provides water and wastewater services for more than 1 million people in the Greater Calgary area. For many municipalities, accurate and regular condition assessment of large-diameter pressure pipelines has become more important in recent years as these assets continue to age and risk of failure increases.
In Calgary, three critical feedermains (14th Street/North Hillhurst, John Laurie and Top Hill) are each constructed of different materials: lined cylinder pipe (LCP), prestressed concrete cylinder pipe (PCCP) and bar wrapped pipe (BWP). The pipes range from 750mm (30-inch) to 900mm (35- inch) in diameter.
|PureRobotics® electromagnetic condition assessment
PureRobotics® HD-CCTV inspection
|PCCP, LCP, BWP|
|4.74 km (2.9 miles)|
|750mm-900mm (29-35 inch)|
Condition assessment on 2.92 miles (4.7 kms) of feedermain pipes
Data identified 8 pipes with electromagnetic anomalies consistent with broken pressing wire wraps
HD-CTTV identified 3 pipes with damaged internal mortar and exposed cylinder
In data collected from more than 14,000 miles of pressure pipe condition assessment, Pure Technologies has found that only a small percentage of pipes (less than 5 percent) are in need of repair and therefore have years of service left. Condition assessment data also suggests that pipe distress is localized, and significant ROI can be achieved by locating and addressing isolated problems through structural inspection.
In BWP, the technology identifies and locates broken bars and areas of corrosion on the steel cylinder, which are the main indication this type of pipe will eventually fail. Although BWP looks similar to PCCP in cross section, the design and materials are significantly different.
PCCP is a concrete pipe that remains under compression because of the prestressing wires, with the thin-gauge steel cylinder acting as a water membrane. With BWP, the cylinder plays a much larger role in the structural integrity of the pipe. BWP is essentially designed as a steel pipe with mild steel used to manufacture the steel cylinder and steel bars. PCCP utilizes mild steel for the cylinder, but high strength steel is utilized for the wire, which is wrapped under high tension. As a result, the bar in BWP and wire in PCCP respond differently to environmental conditions that facilitate corrosion.
The high strength steel wire in PCCP is smaller in diameter and wrapped under higher tension, therefore corrosion makes it quite vulnerable to breakage. The mild steel bars in BWP are thicker in diameter and wrapped under less tension, therefore corrosion takes significantly longer to lead to breakage. The type of failure is also much different; PCCP tends to fail suddenly with a large dispersion of energy. This type of failure is less likely in BWP where failures are similar to steel pipe with long periods of leakage occurring prior to rupture. Because of the differences in make-up, BWP and PCCP are inspected using unique methods to determine their structural condition.
Evaluation of the John Laurie Boulevard Feedermain concluded that one (1) pipe was identified to have an anomalous signal likely caused by a non-uniform cylinder. Images obtained from the robot indicated this pipe has damaged internal mortar and exposed cylinder. Additionally, two (2) pipes on this feedermain were identified to have damaged internal mortar and exposed cylinder, but did not contain anomalous signals.
The City of Calgary was pleased with the results, and through condition assessment, has been able to identify and address individual distressed pipe sections on otherwise serviceable feedermains. This has allowed the City to avoid potential ruptures, while increasing service reliability and useful life of the feedermains.